Standard exchange of the product, including the battery module, if it proves to be defective.
Tower UPS, 6 kVA, standard module (Power module + 1 Battery module), 3.9 kW output power, EMC Level B + EPO
◗ UPS and battery fully interchangeable on-line: thanks to the manual bypass, there is no interruption of the power supply to the protected position during replacement of the UPS or the battery.
◗ In addition to the manual bypass, the Comet EXtreme is equipped as standard with an automatic bypass which transfers the load to the mains supply in the event of an overload or a fault.
◗ No demand on the batteries over a wide range of input voltages (85 to 265 Volts).
Choice of battery capacities
◗ Standard battery capacity ranging from 20 minutes (at 70 % load) up to several hours with battery extension modules.
◗ Very long endurance (up to 8 hours at full power) with the CLA charger module.
Protection for equipment which is sensitive to electromagnetic interference:
Comet EXtreme conforms to the most stringent EMC standards (Level B):
◗ standard version: rack format,
◗ optional tower format.
Perfect integration into service sector environments
◗ 8 U (1 x 4 U battery module + 1 x UPS 4 U module) for the 4.5 and 6 kVA versions.
◗ 13 U (2 x 4 U battery modules + 1 x UPS 5 U module) for the 9 and 12 kVA versions.
◗ Compatible with racks from 600 to 900 mm deep.
◗ Optional Comet PDU: IEC 10 A and 16 A terminal block to facilitate electrical distribution in the rack (electrical panel not required).
◗ Less than 450 mm high, the Comet Extreme can easily be installed beneath a console table, a reception desk or in a power room.
Visual and audible check
LEDs and an audible alarm on the front panel of the Comet EXtreme provide instant identification of the alarms and rapid verification of the status of the UPS.
Solution-Pac software suite supplied on CD with each unit
To control the protected servers (clean shutdown) and for local or remote supervision of the UPS.
Management-Pac 2 software suite on CD
NMS integration kit: HP Openview, IBM Tivoli Netview, CA Unicenter, etc.
SNMP/Web network card
To connect the UPS to the Ethernet 10/100 network, to relay SNMP warnings and to supervise the UPS via a single Web interface.
Environment Sensor for the SNMP/Web card SNMP and Web monitoring of Temperature & Humidity & the status of 2 contacts.
To connect the UPS to a building management system.
Status information card
To relay the status of the UPS in the form of free potential contacts plus emergency stop.
Remote LCD display for controlling the UPS
To remotely locate the interface of the UPS up to 25 m and to display its parameters.
Eaton Comet EXtreme tower UPS, 6 kVA, standard module. Potenza in uscita: 6000 VA, Potenza in uscita: 3900 W. Tecnologia batteria: Acido piombo (VRLA), Tempo di salvataggio minimo a mezzo carico: 23 min, Tempo di salvataggio minimo a pieno carico: 9 min. Fattore di forma: Torre. Certificazione: EN 50091-3; EN 50091-1; IEC 60 950. EMC: EN 50091-2; EN 55022/B,EN 55011/B, IEC 61000-4, IEC.... Peso: 62 kg